COTUIT WATER DEPARTMENT DRINKING WATER VIOLATION JULY 2013
Our water system recently violated a drinking water standard. Although this incident was not an emergency, as our customers, you have a right to know
what happened and what we did to correct this situation.
From 7/1/13 to 7/31/13 we took twenty-nine (29) samples to test for the presence of coliform bacteria. Three (3) of those samples showed the presence of coliform bacteria. The standard is that no more than one (1) sample may do so.
What should I do?
- You do not need to boil your water or take other corrective actions. However, if you have specific health concerns, consult your doctor.
People with severely compromised immune systems, infants, and some elderly may be at increased risk. These people should seek advice about drinking water from their health care providers. General guidelines on ways to lessen the risk of infection by microbes are available from EPA’s Safe Drinking Water Hotline at l (800) 426-4791.
What does this mean?
This is not an emergency. If it had been you would have been notified immediately. Total coliform bacteria are generally not harmful themselves. Coliforms are bacteria which are naturally present in the environment and are used as an indicator that other, potentially harmful bacteria may be present. Coliforms were found in more samples than allowed and this was a warning of potential problems.
Usually, coliforms are a sign that there could be a problem with the treatment or distribution system (pipes). Whenever we detect coliform bacteria in any sample, we do follow-up testing to see if other bacteria of greater concern, such as fecal coliform or E. coli, are present. We did not find any of these bacteria in our subsequent testing. If we had, we would have notified you immediately. Further testing shows that this
problem has been resolved.
What happened? What was done?
On 7/8/13 nine (9) samples were taken and one (1) came back positive for total coliform (West Street tank). On 7/10/13 repeat samples were taken at that location and designated upstream and downstream locations. The repeat samples came back absent of total coliform. On 7/15/13, eleven (11) samples were taken and one (1) came back positive for total coliform. (Clamshell Cove Rd). On 7/17/13 repeat samples were taken at that location and designated upstream and downstream locations. The upstream sample came back positive for total coliform. The Department flushed the area and ran bleeders for forty-eight (48) hours. On 7/22/13 repeat samples were taken at all three locations. All came back absent of total coliform.
For more information, please contact Chris Wiseman at 508-428-2687 or at the Cotuit Water Department, located at 4300 Falmouth Road in Cotuit.
Please share this information with all the other people who drink this water, especially those who may not have received this notice directly (for example, people in apartments, nursing homes, schools and businesses). You can do this by posting this notice in a public place or distributing copies by hand or mail.
This notice is being posted by the Cotuit Water Department, PWS #4020003, on August 5, 2013.